Roll out of VV Power Solution to support Warranty Claim
Newton Downs solar park failed its due diligence. The acquiring party’s electrical team suspected issues with harmonics, based on snapshot measurements. VoltVision installed a monitoring system across the solar park to cover two sub stations.
After one month of data extraction and analysis, VoltVision’s charting showed a direct relationship between busbar temperature and load, indicating a resistive fault on an internal joint in the transformer.
The data was used by Newton to prove a warranty claim against the manufacturer forcing a replacement event. VoltVision continues to assist in the management of the transformer, preventing catastrophic failure while the replacement is manufactured and delivered.